Model Name : 1W340F
Application fields: industrial environment temperature & humidity real-time detect
1.own display screen ,able to real-time display the temperature & humidity data ,and device info.
2.Software on PC in local area network can real-time read the environment temperature and humidity data, and save related data as files.
3.software support window system
4.POE power supply, compatible with 802.3 af standards.
New Functions !!
(1) 1W340 products newly added Android APP, support all Android phones and tablets. Just download this software1W340_Android_V1.0.zip,
1W340 product Newly add remote access function , welcome to download the newest software (1W340 V4.0 zip) .
Operating steps: 1. Search Device >> 2. Register Account >>3. Login user >> Set device config >>4. Search network device
1.Working voltage：DC 5V
(1)IP address: 192.168.1.188 (the user can modify)
(2)The subnet mask: 255.255.255.0 (the user can modify)
(3). The gateway: 192.168.1.1 (the user can modify)
(4). Connection types: TCP (default shall not modify)
(Device supports secondary development, the details please consult the salesman)
Device using aviation plug connecting internal circuit board, probe and network port. Please tighten the aviation plug, and then connect the switch that support POE with the cable. Device can work( Note: You must insert the plug before power-on).
Connect device to computer with one cable, generally called direct connection or point-to-point connection. It makes it easy to visit device, wire and opera.
Note: The device supports POE power supply mode only.
Factory default IP (192.168.1.188) subnet mask (255.255.255.0) gateway (192.168.1.1).Computer and device must in the same network segment .
Steps as follows:
Step one: "Network Place" -> 'Check the local connection" ->"Local Connection", right click the "Local Connection"->"Properties"
Step Two: "This connection uses the following items" ->"Internet Protocol Version (TCP/IP)"->"Properties"
Step three: Select "Use the following IP address", fill in the subnet mask, default gateway same to the device. Set the IP as 192.168.1.xxx, the final data (xxx) of device IP and the computer IP can not be same (note : xxx don't set 0 or 255)，Set up and then click "ok", save.
The device and the computer have only one network port, if the user wants to visit several devices, or use several computers to visit one or more devices, it requires the user to form a network, the user needs to choose the switch supports POE. There must be more switch ports than the devices.
If the computer and the device is not in the same network segment, users need to modify the IP, subnet mask, gateway to fit with current network, please refer to the device software setting
2.3 Restore factory settings
If you forget the parameters or incorrectly set to make it not work, you can press the Preset button on device for 3~5 seconds. It is finished when the LINK and ACK light go out.
3. Device display
own digital tube ,able to real-time display the temperature and humidity data and device info.
3.1 temperature and humidity data display
aa.bbCx or aa.bbHx
aa.bb is the temperature or humidity value. x is the probe number , C shows the current data is temperature data. H shows the current data is humidity data.
3.2 device info display
after showing the temperature and humidity data of each probe ,the digital tube will show the IP address and the working voltage, such as -192.168.1.188-3.1U.-. For the device has only six digital tube, the device info will show in scrolling display mode.
Besides, user should know the phenomenon of digital tube flash point and pause is common ,for the device continuously read data from each probe.
if the device has no probe plugged in or the probe connection is loose, digital tube of the device after power on ,will show "S-NONE", now you should check the probe connected or nor or connection loose .
if pull out the probe when the device in working, the digital tube will show the wrong data from related probe terminal.
when digital tube prompts "ERR", please check the probe. Restart the device if necessary.
4. Data detection
The resolution and precision of the data will be different by different probes. Please refer to the table below
5.Software instructions (Note: Our software only support windows system .)
5.1. Search probe
Open software will appear the following window, fill in equipment starting the IP address and ending IP address, then , software will search the device from starting to end the IP address .(including all the 1 W340 equipment )
5.2. Real-time temperature
Click on "real-time data” and select IP address what you want to check the equipment. As follow:
Choose what you want to see the equipment IP address and read the temperature (As follows). log default save directory: my document PCsensor 1 W340 V1.3 Data
Choose what you want to see the equipment IP address
Click left mouse button under marquee can zoom curve and narrow curve; Click and hold the right mouse button, can move the curve.
Click on “Setting” and select “General Setting “. As follows:
Click "Setting" and choose "Device Setting" , choose one IP address, as follow:
Click on the HS10, will enter DS18b20 temperature probe to set temperature calibration value.
5.6. MSN remote access to the temperature
MSN users log in, your friends can send related instructions and to obtain the relevant temperature data. When your friends send prompted number 1 to you, he will automatically get the temperature data. Including: real-time temperature, maximum, minimum and average.
5.7. Email function
Fill-mail message, and save. (Send E-mail request: support for POP3/SMTP services or other ports.) Receiving mail can fill two.
Can realize the following functions:
1, open warning function, when the alarm is automatically triggered to send a message to the specified mailbox;
2, you can set the time, from time to time, it will send a message to the specified mailbox (recommended);
3, open continuous send, You can send mail to open a row in the specified mailbox (not recommended).
6. Android APP
6.1 Search the IP or directly add IP address and modify IP address.
6.2 Display the temperature probe Qty and real-time data and Curve.
6.3 Click "Settings" , into parameter Settings.
7. PACK LIST
8. Specification version
9. Copyright statement
Copyright© 2014 by SHENZHEN RDING TECH CO., LTD.
Note: If you want to download the latest software, please click here： http://software.pcsensor.com/pc_en.html
Product Code: 1W340F_D